The Bulkhead Active Chilled Beam is one of Frenger's latest range of high performance Chilled Beams. Energy efficiency has been a key driver for such advancements in Frenger's Chilled Beam Technology.
The Bulkhead beam contains a number of performance enhancing features as can be expected from the Frenger brand. The beam is designed for discreet installation into bulkheads, primarily for use in hotel bedrooms.
Beam Function Principles
Fresh air is supplied to the Chilled Beam where it mixes with reconditioned room air, which is induced through the heat exchanger battery via the return air grille (supplied by installer). The reconditioned and fresh air is then introduced to the room through the air discharge grille (part of the unit supplied by Frenger), comfortably cooling or heating the room as appropriate.
The fresh air can be supplied at a constant volume or have a turn down from 100% of design volume to 60% then 40% of design volume dependent upon room occupancy. Typical supply air pressures are within 40Pa (min) to 120Pa (max).
- Fresh Air Supply.
- Cooled Air Introduced into the Room by the Chilled Beam.
- Warm Air Induced into the Heat Exchanger Battery Via the Return Air Grille.
- Air Discharge Grille.
- Return Air Grille (supplied by installer).
- Water Connections.
If you require any further information, or have a project to discuss, please contact us on +44(0)1332 295 678 or email@example.com as our technical team are here to assist.